LED Panel purification pretreatment
LED panel clean room purify cleanliness is generally over 10000, local partial requirements 1000, some require constant temperature and humidity.Indoor air clean room installation parameters specification required:
|Temperature and humidity requirements||temperature is generally 23 + 2 ºC, relative humidity of 55 + 5%|
|Large fresh air||to ensure that the amount of fresh air per hour indoor ≥40m3 / h|
|Large air||air flow (ventilation frequency is ≥25 times / h)|
|Pressure||the main workshop adjacent room ≥5Pa|
|Average wind speed||100: 0.3-0.5m / s|
|Ventilation times||100,000 ≥18 times; 10000 ≥30 times; 1000≥50 times|
|Floor||use 2mm / 3mm epoxy or PVC flooring, electronic anti-static flooring plant optiona|
1.Intention: Material Airshower is a necessary passage when materials entering the clean room , it can reduce the pollution problems of Materials brought into the clean room.
2.Process: The electronic interlocking doors of the material airshower , and gas can effect chamber to prevent un-cleaned air into the clean room, reducing dust contamination of the clean room during the cargo out of the clean room . When materials into the airshower, high-speed and efficient clean air filter can be spraied to materials by the injection nozzle in all directions.
3. Purposes: to effectively remove dust particles carried by materials, the air with dust particles and re-cycling by the early HEPA filtered into the airshower area.Professionally undertake a variety of clean room solutions, we will be happy to help you